Item NO.: E117
Strong removal of lime, urate, mineral deposits, concrete structures, etc.
Short cleaning time
Condensate line cleaner is used in the cooling tower, condenser, and heat exchanger main scale remover. This product is a pink water agent. When it is cleaned in the pipeline, the color changes to yellow. (The copper and aluminum pipes are better cleaned.) The metal corrosion inhibitor contained in this product ensures that ordinary metal parts are not subject to any corrosion and can prevent rust generation after cleaning. The cleaning time is short and the equipment is safe.
● Fill the system with water and fill it with water.
● For the main machine cleaning, use 1:20-30 times water; clean the whole cooling water system, use 1:30-50 water; clean the whole chilled water system, use 1:100-150 water.
● The drug can be added 3-4 times at intervals of 30 minutes.
● After all the injections of the force-removing force, the pH value will be significantly higher than the initial stage of the operation.
● Cleaning cycle time, the host is about 4 hours; the cooling water system is about 8-12 hours; the chilled water system is about 10-12 hours.
After the cycle, if the force is added again, the water turns red, indicating that it has been cleaned.
● After removing the waste liquid, use a neutralizer to lower the pH by 6-7. This will ensure that the discharged sewage meets national emission standards.
● Rinse the system thoroughly with clean water 1-2 times to remove residue.
● After filling with clean water, add the scale-eliminating scale inhibitor and microbicide fungicide to better maintain the system.
1. Wear rubber gloves and safety glasses when handling. If you accidentally take it, please rinse your mouth and drink plenty of milk or water. If eye or skin contact, please rinse with plenty of water in time. If you are serious, please seek medical advice promptly.
2. Be placed out of reach of children.
3. Protect from light, heat, and pressure during storage and transportation.